Wire with polyvinylchloride isolation for PV3 electrical units on THAT BY 500017371.042-2008
Wires adjusting are intended for electrical units at stationary laying in lighting and power networks, and also for installation of electric equipment, cars, mechanisms and machines on rated voltage to 450 V (for networks to 450/750 B) with a frequency up to 400 Hz or constant tension till 1000 Century.
CONDUCTING VEIN - copper single-wire, copper multiwire.
ISOLATION - PVC plastic compound. The coloring of veins is carried out continuous or drawing two longitudinal strips on isolation of natural color located diametrically. For the wires used only for grounding, isolation has a greenish-yellow coloring
THE NUMBER OF VEINS - 1;
SECTION of VEINS, mm ²: 0,50; 0,75; 1,0; 1,5; 2,5; 4,0; 6,0; 10,0; 16,0; 25,0; 35,0; 50,0; 70,0; 95,0; 120,0; 150,0; 185,0.
Type of a climatic modification of UHL1, HL1, T1 in accordance with GOST 15150.
|Name of a wire||Nominal section,
|PV1||Wire with a copper vein with PVC isolation||0,5-1,0||300/500|
|PV2||Wire with a copper vein with PVC isolation, flexible||1,5-95,0||450/750|
|PV3||Wire with a copper vein with PVC isolation, the increased flexibility||0,5-1,0||300/500|
|PV4||Wire with a copper vein with PVC isolation, high flexibility||0,5-1,0||300/500|
|PV6||Wire with a copper vein with PVC isolation, especially flexible||0,5-1,0||300/500|
* THAT BY 500017371.042-2008
Wires are resistant to influence of temperature surrounding sredyot -50 °C to +70 °C.
The maximum temperature of a conducting vein of a wire 60227 IEC 06 at normal operation-70 oc, 60227 IEC 08 - 90 ° C.
Wires are resistant to influence of mechanical blows, linear acceleration, bends, vibration loadings, acoustic noise, mold mushrooms.
Wires do not extend burning at single laying.
Wires with the RoHS index do not contain lead.
The minimum radius of a bend of a wire at operation has to be not less than ten diameters for wires of PV1 and five diameters - for wires of PV2, PV3, PV4, PV6.
It is long the admissible temperature of heating of veins - no more than +70 °C.
Construction length of wires - not less than 100 m, is allowed delivery by lengths not less than 20 m in number of no more than 10% of party.Average service life of wires - 10 years.